It is very important to check the dry powder fire extinguishing equipment regularly in the fire fighting equipment inspection
月检査内容?1.检査项目ji周qi 下列项目至少mei月检查1次。?干粉chucun装置部件。?驱动气tichu瓶充装量。?2.检査内容 检查干粉chucun装置部件是fu觴in鲎不騤i械xing损shang，防hu涂层是fuwan好;铭牌、标志、铅封应wan好。 对二氧化碳驱动气tichu瓶逐ge进xingchen重检査。
The following items shall be checked at least once a month. Components of dry powder storage device. Drive gas bottle filling capacity. 2. Inspection contents: check whether there is collision or mechanical damage to parts of dry powder storage device and whether the protective coating is intact; Nameplates, marks and seals shall be intact. Weighing and checking the carbon dioxide driven gas storage bottles one by one.
季检的内容和要求 tong过试验fa对泵组shi系tong进xing1次放水试验，检查泵组qi动、主备泵切换ji报警lian动功neng是fu正常。 检査瓶组shi系tong的控zhifa动作是fu正常。 检查管dao和支、吊jia是fusong动，管daolian接件是fu变形、lao化或有裂纹dengxianxiang。
Contents and requirements of the quarterly inspection: conduct a water discharge test on the pump group system through the test valve to check whether the pump group starts, the switch between the main and standby pumps and the alarm linkage function are normal. Check whether the control valve of the bottle assembly system operates normally. Check whether the pipe and support, hanger is loose, whether the pipe connection deformation, aging or crack phenomenon.
(2)年检的内容和要求 定qi测定1次系tong水源的供水neng力。 对系tong组件、管daoji管件进xing1次全面检查，清洗chu水箱、过滤器，并对控zhifahou的管dao进xing吹sao。 chu水箱mei半年换水一次，chu水容器内的水按产pinzhi造商的要求定qi更换。 进xing系tong模拟lian动功neng试验，试验内容yu要求详见第四节第三部分。标zhun要求二氧化碳dafa娱乐网址器mei年至少检查一次，低于额定充装量的95%就应进xing检修。 由于石油化工she备jishou压容器，在温度应力、交变应力、介质强lie腐蚀deng恶劣条件的作用下，容易出xian泄漏，造cheng火灾和中du事故。
(2) contents and requirements of annual inspection: regularly determine the water supply capacity of system water source once. Conduct a comprehensive inspection of the system components, pipes and fittings, clean the water storage tank and filter, and purge the pipes behind the control valve. The water in the storage tank shall be changed every six months, and the water in the storage tank shall be changed periodically according to the requirements of the manufacturer. Carry out the system simulation linkage function test. See the third part of the fourth section for the test content and requirements. Carbon dioxide fire extinguishers are required to be checked at least once a year. Maintenance should be carried out when they are less than 95% of the rated filling capacity. Due to the petrochemical equipment and pressure vessels, in the temperature stress, alternating stress, medium strong corrosion and other adverse conditions, easy to leak, resulting in fire and poisoning accidents
Therefore, every year to do a sampling inspection, when necessary, but also to do 100 percent of the inspection. On the premise of not affecting the external structure of ancient buildings, tall ancient buildings should be installed lightning protection facilities according to the needs of terrain and objects, and the test and maintenance should be carried out before the annual thunderstorm season to ensure good condition and effectiveness.
(3)模拟qi动检査。 2.检査内容 防hu区的shu散tongdao、shu散指示标志和应急照明装置、防hu区内和ru口chu的声guang报警装置、ru口chu的安全标志ji干粉dafa娱乐网址剂喷放指示门deng、无窗或固定窗扇的地上防hu区和地下防hu区的排气装置和门窗she有密封条的防hu区的泄压装置。chucun装装置间的位置、tongdao、nai火dengji、应急照明装置ji地下chucun装置间ji械排风装置。 管网，支jiaji喷放组件 干粉chucun容器的数量、型号和规格，位置yu固定方shi，油漆和标志，干粉充装量，以ji干粉chucun容器的安装质量。 集流管、驱动气ti管dao和减压fa的规格、lian接方shi、布置ji其安全防hu装置的泄压方向。
(3) simulate startup check. 2. Review the content protection the evacuation passageway and evacuation instructions signs and emergency lighting devices, protective zone and the acousto-optic alarm device, the safety sign at the entrance at the entrance and dry powder discharge indicator lamp door, no window sash or fixed protection zone of the ground and underground protective of the doors and Windows with sealing strip and exhaust pressure relief device of protection zone. Location, passageway, fire resistance rating, emergency lighting and mechanical ventilation between storage and installation. Quantity, type and specification of dry powder storage containers for pipe networks, supports and spraying components, position and fixing method, paint and marking, dry powder filling amount, and installation quality of dry powder storage containers. Specification, connection, arrangement and direction of pressure relief of collector pipe, driving gas pipe and pressure reducing valve.
?选择fajixin号反馈装置的数量、型号、规格、位罝、标志ji其安装质量。 fa驱动装置的数量、型号、规格和标志，安装位罝，气动fa驱动装置中qi动气tichu瓶的介质名chen簍ong渥把沽Γ詊iqi动气ti管dao的规格、布置和lian接方shi。 管dao的布罝yulian接方shi、支jia和支吊jia的位罝ji间距、穿过建筑构件ji其变形缝的chu理、各管段和附件的型号规格以ji防腐chu理和油漆颜se; 喷头的数量、型号、规格、安装位置和方向。 dafa娱乐网址控zhi器ji手动、自动转换kai关，手动qi动、停止按钮，喷放指示deng、声guang报警装置denglian动she备的she置。
Select valve and signal feedback device quantity, model, specification, location, logo and installation quality. The e number, model, specification and logo of valve drive device, installation location, medium name and filling pressure of starting gas storage bottle in pneumatic valve drive device, as well as the specification, layout and connection mode of starting gas pipeline. Piping layout and connection, support and hanger position and spacing, through the building components and deformation joints of the treatment, the pipe section and accessories of the model specifications as well as anti-corrosion treatment and paint color; The number, model, specification, installation position and direction of sprinkler head. Setting of fire extinguishing controller, manual and automatic switch, manual start and stop buttons, sprinkling indicator light, sound-light alarm device and other linkage equipment.